Secop Capillary Tube Selection Software
This software allows the user to calculate the measurements of a capillary tube throttling device for a refrigeration system using empirical formulas. The result is a start value for optimization. The start value will result in an acceptable operating system. In certain cases, the best possible choice of capillary diameter and length might deviate remarkably from this calculated result.
The capillary sizing is based on the assumption, that the capillary and suction line is connected to in min. 1 m to make internal heat exchange between liquid and suction gas.
The refrigerant used is chosen from a drop-down list. Input values should be representative values for the refrigeration system.
The input values are:
- Compressor capacity
- Evaporating temperature
- Condensing temperature
- Return gas temperature
- No sub-cooling
The input data are limited per refrigerant according to experience and compressor application areas.
Data such as these could reflect data sheet performance data at ARI 540, EN 12900, or CECOMAF conditions, or others.
The list of capillary tube inner diameters typically includes available sizes from different countries. They will not all be available on one place. A length value for an available diameter size is to be chosen by the user, or estimated, if not listed.
The list of refrigerants and capillary tube diameters and the calculation formulas and limits could be adapted through updates, based on new experience.
Database update 2.2 (2019):
- R600a, updated in April 2018
- R290, not modified since September 2017
- R134a, not modified since September 2017
- R1234yf, not modified since September 2017
- R404A, not modified since May 2006
- R407C, not modified since September 2017
- R507, not modified since September 2017
- R22, not modified since September 2017
- R452A, new since November 2019
- R513A, new since November 2019
Download Capillary Tube Selection Software
Unzip and run "Setup.Exe". Former versions (e.g. DanCap™) must be uninstalled first.